By installing only one WEM3080T (three phase WiFi energy meter) in your single phase solar system, and clamping the first CT onto grid, the second CT onto solar inverter side and the third CT onto load if applicable, you can monitor "From Grid" (the energy consumed from the grid), "To Grid" (the energy imported to the grid) and the energy produced by solar inverter. You can monitor the energy flow of the solar system.
Install the meter on grid side and ensure that the CT direction is correct.
Please refer to Tutorial Video for hardware installation guidance.
Step1, scan the QR code and download the mobile app
Step 2, search and connect the iMeter's access point signal iMeter_xxxxxxxx by your phone
Step 3, Open app and find the iMeter
Tips: If the app prompts "Invalid device version", you need to setup the WiFi network by browser. Same as 3.3 WEM3162T QuickStart
Step 4, Select the SSID of your home WiFi network;
Step 5, Enter password and save. After succesfully configure the WiFi settings, you will see that the IP address allocated for the iMeter.
Tips: SN is the unique Serial Number of your iMeter. You can copy it from the iMeter's access point signal (iMeter_xxxxxxxx, xxxxxxxx is the SN).
Tips: Time zone must be set according to your location for correct data display and report on time basis.
Tips: It is "Single phase" as default meter type in Iammeter system. You need to change the meter "Type" as "Three phase"
Tips: Please set the use type of each CT according to the actual CT installation. For example, if you clamp the CT of phase A onto grid, then you set its use type as "grid".
View on Mobile App
View on Web Cloud
Tips: Please visit https://www.iammeter.com to login to the web portal. Same username and password as app. You can see more analysis report on web.
If you have a WeChat account, please follow our IAMMETER WeChat public ID.
Leave a comment